SPECIFICATIONS: Pre-assembled booth unit shall be Model #75HC, 5’4″ x 7’6″ , as manufactured by Par-Kut International, Inc., Harrison Township, Michigan (586) 468-2947. Unit shall be furnished complete and ready to set in place on the site and shall include the following:
QUALITY: Structure shall be the product of a manufacturer with a minimum of 10 years experience in the design and fabrication of portable steel buildings.
STRUCTURE: Unit shall be all welded galvanized steel construction with 14 gauge steel panels and tubing on the exterior and 18 gauge interior panels and trim. Unit to be shipped completely assembled. Welded joints ground smooth.
BASE AND FLOOR: A.1 – 2″ base height (used in conjunction with a curb cut or ramp). Or, B.1 – no floor, perimeter bar base only, floor to be concrete slab by others. When provided by PAR-KUT, floor surface shall be 12 gauge galvanized steel, 4-way diamond plate. Four anchor clips provided to secure building. Anchor bolts and required installation by others.
PAINT: All exposed metal surfaces except roof top, anodized aluminum window frames and any stainless steel components (if used) shall be painted one color using Axalta® Imron™ high gloss industrial polyurethane. Owner will select a single color from Par-Kut standard colors.
LIGHTING: LED light fixture mounted over counter. Wall mounted on/off switch located 48″ above the floor.
ELECTRICAL: Electrical devices factory installed within the prefabricated building shall be UL listed. Factory installed wiring system shall comply with the current NFPA’s National Electrical Code (NEC). Unit shall be delivered complete with all wiring required for LED light with lamp and switch, one 110V duplex outlet, heater, a 100A 12-circuit load center with branch circuit breakers and 100A main breaker. All wiring copper #12 AWG minimum, enclosed in EMT, rigid, flex or as MC cable. Ready for site connection. Three wire 240/120V single-phase service required.
HEATER: Electric wall heater shall be 120 volt/1500 watt/5120 BTU, including fan and wall mounted thermostat.
OPTIONAL AIR CONDITIONER: Shall be 120 volt/13500 BTU, roof mount, with wall mounted thermostat.
DOOR: Shall be 36″ wide swinging steel door with safety glazing, weather-stripping, heavy duty ball bearing butts and lever handle lockset. Door located in 5’4″ wall opposite the shelf. (Owner responsible for ramp, if required)
WINDOWS: Welded steel frames, all fixed, non operable type. Painted steel construction with removable interior glazing stops. Provide sliding windows as shown on drawings for ventilation and/or transaction purposes. Include insect screens in ventilation windows.
GLAZING: Shall be clear tempered safety glass 1/8″ minimum thickness.
COUNTER: 14 gauge painted steel, 25″ deep, 32″ above floor with 16″ wide steel storage drawer.
INSULATION: Walls insulated with 2″ rigid Fiberglass Board. Roof structure fully insulated.
ROOF/CANOPY: Shall be 14 gauge galvanized steel, pitched for rainwater run-off. Extension beyond side walls shall be 3″. Provide forged steel eyebolt(s) in roof for lifting by crane. Exterior booths include drain pipe. Interior booths to have flat, no overhang roof and removable lift ring when overhead clearance is a problem.
DESIGN LOADS: PAR-KUT booths meet or exceed the following design loads: 50 PSF live load, 30PSF wind load.